Circuit breaker testing with OMICRON
Orlando de Leon, application sales engineer at OMICRON, explains the benefits and new method of testing circuit breakers in Gas Insulated Switchgears (GIS).
9th September 2019 by Networks
During the last few years we have seen an increasing demand for non-invasive test methods for evaluating the condition of circuit breakers. Regardless if the circuit breaker is installed in a conventional substation, a switchgear or a Gas Insulated Substation (GIS), the industry has moved to try to perform a complete diagnostic without intervening any working connection; that means, testing both sides grounded systems and taking measurements without disconnecting secondary cables of the circuit breaker.
With OMICRON’s test system CIBANO 500’s three-in-one approach you only need to set up the wiring connections once, and that allows you to perform all tests in one go. The CIBANO 500 combines a precise micro-ohmmeter, a multi-channel timing analyzer, a powerful coil and motor supply in a single device.
Testing circuit breakers in GIS is a major challenge due to the availability of the bays and having a safe system. The CIBANO 500 offers a patent method to test circuit breakers installed in a GIS – this allows the operating times, motion test, contact resistance, coil and motor current analysis of the circuit breaker to be determined accurately even though the GIS is grounded on both sides. During a closed or open operation of the circuit breaker, the sensor measures the current change through the ground connection of the circuit breaker and sends its signals to the CIBANO 500 which determines the switch response times. Since the new current sensor has a flexible design and can be easily installed on a multitude of different grounding switches, it is ideal for on-site applications in GIS installations.
Login on register to comment
Cadent backs launch of major bio-CNG HGV refuelling station
Gas network’s £250,000 infrastructure investment ensures supplies to existing connected customers have not been impacted
Editor’s blog: The biggest tests of resilience are yet to come
Network content director Jane Gray reflects on the industry's coronavirus response to date and the challenges still to come.
From the front line: Chris Garside and Andy Simcoe, Northern Gas Networks
Key workers across the power and gas networks are playing a critical role in the national response to Coronavirus. Network has committed to profiling their stories.
Related supplier content
Load patterns and lockdown: how Covid-19 is impacting electricity networks
Insights into dynamics on the low voltage network as the outbreak unfolds
Protect electrical equipment from insulation failure
Insulation faults are a major cause leading to the eventual failure of electrical equipment. Partial discharge (PD) is a very reliable indicator of developing insulation faults. Regular PD testing allows users to detect and analyze PD activity
How E.ON. is helping the City of London become a zero emissions city
Discover Citigen. Deep in the heart of our bustling capital