Testing substation circuit breakers safely
Damon Mount, UK and Southern Africa sales manager at Megger, discusses safety and accuracy when testing circuit breakers.
8th October 2019 by Networks
When a circuit breaker requires maintenance it needs to be isolated and grounded on both sides for safety. This can distort the test readings but removing the ground creates a safety hazard. Test instruments with DualGround capability make fast and accurate circuit breaker testing possible with both sides of the circuit breaker grounded.
With DualGround measurements, engineers and technicians are protected against receiving dangerous shocks from voltages induced in the breaker, by current flow in nearby live conductors. This is critically important in the substation environment.
It has been possible to measure timing with both sides of the circuit breaker grounded with dynamic resistance measurement (DRM) techniques, but the results are not always consistent and reliable. Dynamic capacitance measurement (DCM) technology is able to produce dependable timing results safely on all types of circuit breaker including GIS.
Engineers and technicians are protected against receiving dangerous shocks from voltages induced in the breaker
The test configuration for DCM testing is identical with that used for DRM measurements but, instead of looking at resistance changes in the main contact circuit during the operation of the breaker, DCM treats the contact assembly as a variable capacitor. As the breaker operates, the distance between the fixed and moving contacts changes, which means that the capacitance between them also changes. DCM evaluates these capacitance changes and uses them to provide accurate and repeatable timing measurements.
This method significantly increases safety and accuracy and reduces testing time, since it is no longer necessary to remove one of the ground leads before making a measurement and reattaching it afterwards.
For further information email: email@example.com
Login on register to comment
The future for vegetation management
Why networks should focus on data not trees to overcome the costly challenges involved in vegetation management
An unprecedented opportunity for change
Why short interruptions will matter in RIIO-ED2 and how to address them.
Funding for SSEN electric vehicle scheme
Innovation initiative will bring forward portable EV charging devices
Related supplier content
Load patterns and lockdown: how Covid-19 is impacting electricity networks
Insights into dynamics on the low voltage network as the outbreak unfolds
Protect electrical equipment from insulation failure
Insulation faults are a major cause leading to the eventual failure of electrical equipment. Partial discharge (PD) is a very reliable indicator of developing insulation faults. Regular PD testing allows users to detect and analyze PD activity
How E.ON. is helping the City of London become a zero emissions city
Discover Citigen. Deep in the heart of our bustling capital